Long retractable sootblowers periodically require adjustment of head pressure settings to achieve desired steam pressure levels for cleaning. Historically, to adjust head pressure settings, standard poppet valves had to be closed and isolated and the sootblower shut off – oftentimes across the entire bank. The Diamond Power® EAPC™ poppet valve was developed specifically to solve this problem, and has undergone significant design improvements since its first introduction in the 1990s.
The latest EAPC poppet valve design can be adjusted externally, while the sootblower is running, without binding or galling. Laboratory testing provided key information to solve critical friction contact points and surfaces, and to optimize trigger-to-steam contact patterns. Field tests in both utility and recovery boiler environments confirmed trouble-free operation in long-term use under severe operating conditions.
Simple and safe valve adjustment procedure:
The EAPC poppet valve is available as optional equipment on all retractable sootblowers. In addition, the EAPC poppet valve can be retrofitted to any existing Diamond Power retractable sootblower as a replacement part or a rebuild of the current valve.
The EAPC poppet valve is available in two pressure classes: